text: <s>[INST] PF400 - Analog Out2 I have PF400 15kW 30A and my motor rating are 15kW 26A. I wanna use the analog output from PF400 to show the current consumption. Parameter values: P033 = 26A, T085 = setting 15 (4 mA = 0 Amps, 20 mA = 200% Drive Rated FLA) What is Drive Rated FLA? Is that the value i entered in P033 or the drive rated current? What kind of scale should i use 0-60A or 0-52A to show the correct consumption? [/INST] Drive FLA, is the rated current output of the VFD, so in your case it would be the 30A. So, your analog output would show values ranging from 0 - 60A without adjusting the scaling in T086. If you look at the examples in the manual for T086, you will see how adjusting the scaling will adjust the range of the output displayed. \\n </s>