text: <s>[INST] PowerFlex 40 Control from Terminals or 22-COMM-E Summary: A051[6] , P36 ,P38We need a Powerflex 40 to Remote start/reference from 22-Comm-e . Local start/reference from terminals If AO51 =6 and input hi does 22-comm-e control VFD? If A051=6 and input lo does P36 and p38 control VFD? Thanks [/INST] Yes, it will work as needed. There is a similar example inside Aid 47161. - fuzzy logic In order to enhance Forum's contributors reputation, please rate the replies you got and remember to close the thread clicking Choose as Best Answer button over the solving answer. Thanks ! \\n </s>