text: <s>[INST] PF700 Analog Output I have a project where I am reading output power from a PowerFlex 700 series A VFD (part number 20B D 077 A 3ANNANA0) over the analog output connection. I am scaling this value between 0 and 90 kW. My customer complains that at a no load situation the display from this scaling will be around 1.5 kW, while the HIM will display about .8 kW. If this is normal can you help me with an explanation? [/INST] DMM, it would be helpful to know how the parameters related to the analog out have been configured (i.e. par# - value) and also some informations about the analog in you use (is it a PLC module, which, which input range etc.). The more infos you put into your posts, the more help you can expect to receive from other users... :smileywink: - fuzzy logic \\n </s>