text: <s>[INST] Configuring 527 for fan motor application I am currently adding a 527 drive to a L71S PLC via ethernet. I am trying to configure the motion group and I need to know what settings I will need in setting up the axis. [/INST] If you already have the drive configured in the IO tree, you should also have an axis associated with it. In the motion group folder, create the motion group using right click / create. Name is unimportant. Move the axis from the ungrouped folder to your new motion group. Doubleclick it to open its property page. You've given us little information to go on, so I'm going to make wild assumptions on what you have - like, no feedback. General tab: Axis configuration - pick frequency control Motor tab: Data source - nameplate data sheet motor type - rotary induction Fill out the motor parameters. Do make sure you get pole count correct - Poles = 120 x base frequency / synchronous speed Analyser tab: Run this after you have wired, powered, and communicating. Dynamic test by preference, but static test will work. Hookup test tab: Use that to verify correct rotation Frequency control tab: Go with defaults until you know what you want to adjust. Drive parameters tab: Pick what parameters you want to have access to read and write. You cannot have them all. Pick the monitoring ones that make sense for your application to display on an HMI. \\n </s>