text: <s>[INST] PF 400 Fan & Pump Ratings Summary: Trying to understand the different drive ratingsGreetings all, I recently sold a 10hp and 2 x 15hp 208V PF400 Fan & Pump drives only to have my customer come back and tell me that I have undersized the drives. The motor FLA's are 32.7A and 47.8A respectively. Their case is that even though the part numbers on the drive indicate that they drives are 33A and 49A output capable, however in the technical data guide, in the F&P section it states the drives have a 30.8A and 46.2A output. My question is, how is this possible? See clips of the two ratings below. Please help. Standard Drive Rating F & P Drive Rating [/INST] I believe the numbers you're looking at are on page 37, which are for configured drives. Did you sell these as configured or just open type stand-alone drives? \\n </s>