text: <s>[INST] Devicenet error code E#78 I have a devicenet network with 3 nodes. Two of my nodes are Allen-Bradley bulletin 160 drives and the other is a Mettler-Toledo IND 560 weighting terminal. The problem is that i always get the error code E [/INST] Sometimes it is possible to solve communication timeouts (error 78) increasing the Interscan Delay in the DNB properties (RSNetworx)... let's say 20 / 30 / 50 ms ..and see what happens...:smileytongue: I don't know the IND 560, anyway if possible do not use the Autobaud in this device, just set the correct network speed directly... Also verify the possibility to download a newer firmware in this device, sometimes that solves... Hope this helps… - fuzzy logic \\n </s>